Blauberg Clean Box 125 G4-F8
- Designation key
- Additional diagrams
- Replaceble filters
For purification of supply air in ventilation and air conditioning systems installed in various premises. Suitable for limited mounting space. Compatible with Ø 100 up to 200 mm round air ducts.DESIGN
The casing is made of polymer-coated steel. Easy access for filter maintenance.MOUNTING
Due to compact design is the ideal solution for mounting in limited spaces, including the space behind false ceiling. Any mounting position. Wall or ceiling mounting with fixing brackets supplied as a standard.AIR FILTRATION
Built-in filters provide efficient air filtration. Up to three filters can be installed into the casing. G4 filter provides primary filtration. At the second stage, the secondary filter F8 or HEPA filter H13 can be installed. F8 filter arrests up to 98 % of PM2.5 dust particles. H13 filter arrest up to 99 % of PM2.5 dust particles, pollen and bacteria. For additional elimination of odors and gases carbon filter can be installed. Quick access to replaceable filters through service panel.
The UV lamp with a wavelength of 256 nm cleans the air passing through the filter box from viruses and bacteria. The detachable lamp unit can be easily removed for maintenance or replacement thanks to a special service panel. The service life of UV lamps is up to 8000 hours.
The Clean Box ES is equipped with an electrostatic filter that enables purification of air from fine dust and soot, spray, smoke and other particles with the size of 0.01 microns and less. By default, models with an ES electrostatic filter are supplied with G4 preliminary filters. Max. filter cleaning efficiency 98 %. The electrostatic filters rely on gravity of oppositely charged objects. The polluted air stream flows through the spray charging unit for the particles ionization. Ionized particles are moved by the airstream and accumulated on the collecting plates which are oppositely charged.
The filter cleaning interval depends on the inlet air pollution density and may vary from 7 up to 21 days. The filter cleaning interval is determined by the visual inspection of the filters. Vacuum cleaning is allowed.APPLICATION
|Parameter||Clean Box 125 G4-F8||Measurement unit|
|Casing material||polymer-coated steel||-|
|Air duct||for round air ducts||-|
|Mounting||ceiling mounting, wall mounting, flush mounting||-|
|Series||Duct diameter [mm]||Filters||UV lamp|
|Clean Box||100; 125; 150; 200||G4; G4-F8; G4-F8-Carbon; G4-H13; G4-H13-Carbon; ES||UV|
|Model||Overall dimensions [mm]|
|Clean Box 125 G4-F8||125||413.5||249||415||513.5||508|
|Clean Box 125 G4-F8|
|G4 Panel filter||FP 220x400x47 G4|
|F8 Panel filter||FP 220x400x47 F8|