- Connection diagram
Self-calibrating sensor with microprocessor control for measuring carbon dioxide content in the air within the range from 0 to 2.000 million-1 (parts per million).MOUNTING
The sensor is mounted onto a wall or a mounting box inside the serviced space. The unit is powered from a 24 VAC/VDC low-current electric mains.
DPWQ40200 CO2 sensor has 2 analogue outputs: 0–10 V and 4–20 mA. An analogue output provides for stepless fan speed control (requires an EC motor fan or a frequency drive). With stepless control the fan speed is changed in proportion to carbon dioxide concentration changes. The CO2 content in the air is measured by means of a non-dispersive infrared analyser (NDIR).
|Power source||24 V AC/DC||-|
|Gas analyser||optical (NDIR)||-|
|CO₂ measurement range||0-2,000 million– ¹ (parts per million) of CO₂||-|
|CO₂ output signal||0-10 V||-|
|CO₂ measurement precision||± 30 million– ¹ (parts per million), ± 5% of maximum value||-|
|Ingress protection rating||IP55||-|