Blauberg FRESHBOX E1-100 ERV WiFi
- Capacity diagram
- Ecodesign parameters
- Designation key
Efficient solution for supply and exhaust ventilation of enclosed spaces.Electric pre-heater or re-heater modification available for cold climate conditions.Heat exchanger with an enthalpy membrane modification available for humid and hot climate conditions.Low-energy EC fans.Silent operation.Supply air purification ensured by two built-in G4 and F8 filters (optionally H13 filter).Upgradeable with an exhaust duct to provide air extraction from the bathroom.Easy installation.Compact size.Wi-Fi communication.Controlled by Android or iOS smartphone or tablet over Wi-Fi.
Polymer coated metal casing decorated with an acrylic front panel. Heat and noise insulation is ensured by a layer of 10 mm cellular synthetic rubber.
The units feature efficient electronically commutated (EC) motors with an external rotor and impellers with forward curved blades. These state-of-the-art motors are the most advanced solution in energy efficiency today.
|AIR DAMPERS||HEAT AND ENERGY RECOVERY|
The unit is equipped with supply and exhaust air dampers which activate automatically to prevent drafts while the unit is off.
Supply air cleaning is provided by the G4 and F8 filters. To meet more stringent air purity requirements the F8 filter can be replaced with an H13 Filter (purchased separately). Exhaust air is cleaned by the panel filter G4.
The cold outdoor air passes through the filters and the heat exchanger and then is delivered to the serviced space by the supply centrifugal fan.
The Freshbox 100 WiFi units are equipped with a counter-flow heat recovery core with a polystyrene core.
The Freshbox 100 ERV WiFi units are equipped with a counter-flow energy recovery core with an enthalpy membrane at the core.
Freshbox E-100 WiFi, Freshbox E2-100 WiFi units are equipped with an electric pre-heater for freeze protection of the heat exchanger.
Freshbox E1-100 WiFi, Freshbox E2-100 WiFi units feature an electric re-heater to raise the supply air temperature as necessary.
Freshbox 100 WiFi features an exhaust air temperature sensor downstream of the heat exchanger which disables the supply fan to let the warm extract air warm up the heat exchanger. After that the supply fan is turned on and the unit reverts to the normal operation mode.
Each space requiring ventilation is equipped with one or several Freshbox 100 WiFi units.
Freshbox 100 WiFi units can be upgraded with a bathroom exhaust air duct. To enable such a configuration the units can be additionally equipped with the optional ø 100 mm spigot (supplied as standard).
|FRESHBOX 100 WIFI DEPLOYMENT IN A COMPACT RESIDENTIAL SPACE|
|FRESHBOX 100 WIFI MOUNTING EXAMPLE IN THE OFFICE|
|Parameter||FRESHBOX E1-100 ERV WiFi Speed IV||FRESHBOX E1-100 ERV WiFi Speed V||FRESHBOX E1-100 ERV WiFi Speed I||FRESHBOX E1-100 ERV WiFi Speed II||FRESHBOX E1-100 ERV WiFi Speed III||Measurement unit|
|Max. power without electric heater||37||53||20||23||29||W|
|Max. unit current without electric heater||0.4||0.4||0.4||0.4||0.4||A|
|Sound pressure level at 3 m distance||33||39||13||20||27||dBА|
|Max. operating temperature||-25...+50||-25...+50||-25...+50||-25...+50||-25...+50||°С|
|Heat recovery efficiency||89||87||90||94||92||%|
|Heat exchanger type||counter-flow||counter-flow||counter-flow||counter-flow||counter-flow||-|
|Remote control panel||Sensor Wi-Fi||Sensor Wi-Fi||Sensor Wi-Fi||Sensor Wi-Fi||Sensor Wi-Fi||-|
|Functions||Wi-Fi, Filter replacement indication, Timer, Weekly schedule||Wi-Fi, Filter replacement indication, Timer, Weekly schedule||Wi-Fi, Filter replacement indication, Timer, Weekly schedule||Wi-Fi, Filter replacement indication, Timer, Weekly schedule||Wi-Fi, Filter replacement indication, Timer, Weekly schedule||-|
|Heat exchanger material||enthalpy||enthalpy||enthalpy||enthalpy||enthalpy||-|
|Connected air duct diameter||100||100||100||100||100||mm|
|Heating||electric reheating||electric reheating||electric reheating||electric reheating||electric reheating||-|
|Casing material||polymer coated steel||polymer coated steel||polymer coated steel||polymer coated steel||polymer coated steel||-|
- Selection method:
- Air capacity:
- Air capacity: --
- Pressure: ---
|Model||Heater||Nominal air flow [m³/h]||Heat exchanger core type||Control|
_: no heater
|-||100||_: standard type
|WiFi: Wi-Fi communication|
|MS Freshbox 100 chrome||
|MS Freshbox 100 white||
|AH Freshbox 100 chrome||Ventilation outer hood made of polished steel|
|AH Freshbox 100 white||Ventilation outer hood, painted white|
|EH Freshbox 100||Heater to prevent condensate freezing in the drain pipe and outer ventilation hood|
|FP 193x158x18 G4 PPI||G4 Filter|
|FP 193x158x47 F8||F8 Filter|
|FP 193x158x47 F8 C||F8 Carbon Filter|
|FP 193x158x47 H13||H13 Hepa Filter|
|CD-1||CO2 Sensor with LED lights for indication of CO2 concentration and a touch button for operation mode switching