Supply air cooling for ventilation systems in various premises. Suitable for installation into supply ventilation or into air handling units to provide air cooling.
Galvanized steel casing. The cooling elements are made of copper tubes and aluminum plates. Available in three-coil modifications and rated for maximum operating pressure 1.5 MPa (15 bar). Polypropylene droplet separator and drain pan for condensate drainage and removal included. Droplet separator is efficient at an air flow not exceeding 4 m/s.
|Counter air flow connection
|Air flow streamwise connection
Only horizontal mounting by means of flanged connection. Air evacuation and condensate drainage must be provided. Air filter installation upstream of the cooling unit to prevent the unit soiling. Installation position must ensure uniform air flow distribution in the section. Mounting upstream or downstream of the supply fan. The minimum air duct length downstream of the fan must be 1 m to ensure air flow stabilization. The maximum cooling capacity is attained if the cooling unit is connected on counter-flow basis. The attached charts are valid for counter-flow connection. If water is used as a cooling agent, the cooling unit is suitable for indoor use only with the ambient temperature not below 0 °C. If antifreezing solution, for example, ethylene glycol solution, is used as a cooling agent, the cooling unit is suitable for outdoor use as well. While mounting the cooling unit provide condensate drainage through the U-trap. The U-trap height must be selected with respect to the total fan pressure, refer to the table and diagram below.
H – U-trap heightK – drain heightP – total fan pressure
For a proper and safe operation of the cooling unit it should be connected to a control system for integral control and automatic cooling capacity regulation.