For arranging warm air distribution system from chimney room to other rooms.For heating of occasionally or seasonally occupied buildings.Operating temperature from 0 to 150 °C.Compatible with Ø 125 up to 160 mm round air ducts.
Atmospheric resistant galvanized steel casing and impeller.Thermal and heat-insulation with non-flammable mineral wool.The casing is perforated for internal air circulation for cooling the motor down.The casing has fixing for connection of extra options (filter, mixing chamber, bypass system).Power is supplied to the fan through an external terminal box with sealed electric lead-in.Switches on and off at set temperatures. Regulation by built-in temperature regulator.
AF – metal filter-box for air purification. Filter class G3.KF – metal mixing chamber for cold air supply. The chamber includes a temperature regulating damper and filter for air purification. The chamber provides cold air supply when the air temperature exceeds 90°C and hot air removal when the fan is off.GF – gravity damper prevents air back draft into the system and together with mixing chamber KF provides by-pass motor overheating protection. When the fan is off, e.g. during power cut-off the gravity damper is closed and warm air is distributed through the mixing chamber and connected air ducts to other rooms.
Suitable for installation in any mounting position with respect to air flow direction in the system.Warm air distribution from the fan to other premises through the mounted air ducts.
Single-phase asynchronous motor. Centrifugal impeller with forward curved blades.The Kamin-ER fan is equipped with an external rotor motor.The motor is placed off the air flow and is equipped with extra axial impeller for motor cooling and blowing off.Motor insulation class F.Equipped with ball bearings for longer service life.Dynamically balanced turbine.Overheating protection by built-in thermal switches with automatic restart.
Smooth speed control with an external thyristor controller or step speed control with an external auto transformer (both available upon separate order).
OPERATING LOGIC OF THE FAN KAMIN WITH AF FILTER-BOX
OPERATING LOGIC OF THE FAN KAMIN WITH BY-PASS SYSTEM