Blauberg Valeo-BP 75/100
- Capacity diagram
Extract ventilation systems installed in high-rise buildings and premises.Mono-pipe ventilation systems.For mounting in kitchens and bathrooms.Flush wall or ceiling mounting.
The fan consists of the plastic casing BP for flush mounting and exhaust ventilation unit Valeo with a flat front panel.The casing is made of durable ABS plastic and fitted with a gravity backdraft damper to prevent backdraft.The front panel is made of snow white UV-resistant plastic.G4 purifying durable filter protects the motor, impeller and ductwork system against soiling.The filter is easily accessible for service operations.Due to modern design and various colour modifications the front panel matches well with any interior.The casing is equipped with oblong slotted joints to facilitate mounting of the casing in true vertical position.If the casing is installed with some vertical deviations, the special turnable grille conceals possible mounting inaccuracies.Power is supplied to the fan through a sealed electric lead-in on the casing and the ventilation unit is equipped with an airtight terminal block for connection to the wiring system.For room-to-room ventilation some ventilation unit modifications are equipped with extra spigots: Valeo-BPL – on the left; Valeo-BPR – on the right; Valeo-BPD – on the bottom.Ingress protection rating IP55.
Two-speed motor with a centrifugal impeller. Minimum energy demand.The impeller has forward curved blades.Automatic maintaining of constant air flow depending on variable air resistance of the duct.Balanced impeller ensures low noise operation.Best aerodynamic characteristics due to a special scroll casing design.Ball bearings provide long service life.The ventilation unit with the motor is fixed inside the casing with special latches.
Step speed control with an external speed controller, e.g. a CDP-3/5 model which is available upon order.Wide range of intellectual controls programmable by set parameters (timer, adjustible timer, internal switch, humidity sensor).
Installed in a wall or ceiling during general construction works by mounting brackets supplied as a standard.Connection to the main ventilation shaft with flexible air ducts.For exhaust ventilation of a neighbour room remove a plug and install an additional spigot. Available upon separate order.Exhaust spigot diameter 80 mm.Power is supplied to the fan through a sealed electric lead-in on the casing.After installation works cover the unit with a protecting cover to prevent dirt ingress.After finishing works install the ventilation unit inside the casing and connect it to the wiring system.
|HIGH-RISE MONO-PIPE VENTILATION SYSTEM ARRANGEMENT EXAMPLE|
The mechanical centralized mono-pipe exhaust ventilation system for kitchens and bathrooms based on Valeo-BP fans is specially designed for high-rise residential premises.Fresh air is supplied to bedrooms, children's room or living rooms through windows or wall vents. Vent modifications with air volume regulation are available.
Stale air is extracted from the room by the exhaust fans through the inside doors or door grilles in the kitchen, bathroom or WC.This ventilation system arrangement ensures non-stop controllable air circulation in the room, comfortable microclimate and high fire safety.
|1 – Exhaust fan Valeo-BP with extra spigot for – room-to-room ventilation.2 – Exhaust fan Valeo-BP.3 – BLAUBERG wall grille, DECOR series.4 – BLAUBERG wall vent, WHM series.5 – BLAUBERG window vent, FHM series.6 – BLAUBERG ventilation door grilles, DECOR series.7 – Central ventilation shaft.8 – Flexible air ducts for connection of exhaust fans to the central ventilation shaft, e.g. BLAUBERG air ducts, BlauFlex series.|
|Cable cross section||3x1.5||3x1.5||mm²|
|Maximum air flow||75||100||m³/h|
|Maximum air flow||21||28||l/s|
|Motor IP rating||IP55||IP55||-|
|Max. operating temperature||+50||+50||°С|
|Air duct||for round air ducts||for round air ducts||-|
|Mounting||ceiling mounting , wall mounting||ceiling mounting , wall mounting||-|
|*||Sound pressure level measured in free space at a distance of 3 meters from the fan||Sound pressure level measured in free space at a distance of 3 meters from the fan||-|
|Sound pressure level||29*||38*||dBА|
- Selection method:
- Air capacity:
- Air capacity: --
- Pressure: ---
|Modification name||No extra functions|