Blauberg WMG 1-10
- MIXING UNIT CALCULATION DIAGRAM
Smooth heating medium flow regulation and supply air set temperature maintaining in ventilation systems with water heating or cooling coils.Compatible with the WKH duct water heating coils and the KWK duct cooling coils.
CONNECTION TO WATER CIRCUIT
Connection of the mixing unit to the water heating or cooling coils and to the water heating/cooling network through the pipes or flexible hoses of respective diameter, refer to the technical data table. In case of applying flexible hoses the mixing unit must be rigidly fixed. While installing the mixing unit the motor shaft must be installed horizontally. No mechanical loads from the pipes are allowed.
The water mixing unit consists a circulation pump, a three-way electrically actuated heat medium control valve and a recirculation pipe.
The three-way valve is designed for smooth mixing of the heat medium stream from the heating (cooling) system and the return heat medium in a required proportion to regulate the heat medium temperature supplied to the water heating or cooling coils. The three-way way is actuated with a control 0-10 V signal from the ventilation control system. The mixing unit is rated for heat medium operating pressure in the mixing set 10 bar.
|Parameter||WMG 1-10||Measurement unit|
|Number of pump speeds||3||-|
|Transported heat medium temperature||-10 +110||°С|
|Max. glycol content in the transported heat medium||30||%|
|Circulation pump||DAB A50/ 180XM||-|
|Max. pump power||184||W|
|Three-way valve control way||0…10 V||-|
|Electrically actuated three-way valve||R323||-|
|Three-way valve heat medium transmission factor (Kvs)||10||-|
|Three-way valve actuator Belimo||LR24A-SR||-|
|Max. mixing unit flow capacity||6.0||m³/h|
|Connection type||Threaded connection||-|
|MIXING UNIT CALCULATION DIAGRAM
Mixing unit selection: find the required heat medium flow through the heating (cooling) unit as well as heat medium pressure drop (available head). These parameters are determined using the heating or cooling unit calculation diagram for each water heating or cooling unit.
|RECOMMENDED CONNECTION TO WATER NETWORK
T1 and T2 – heat medium supply and return pipeline;